Re: IEC 60601 Testing - Section 13.2.7 - Impairment of Cooling
Thank you for your response, You gave the same interpretation, as I thought. Actually we are developing products, which will be connected to medical devices (producing medical systems) and we really want to satisfy the needs of this market, so we decided to take the more strict medical regulations. Our risk management still not prepared enough to meet the requirements of ed 3rd. so until we develop it, we take 2nd ed. as a very first step. Also there is this nrtl mark problem in the states, we can wait the recognition of 3rd.
The real question is that how to manage to keep the temperature low, while the airflow is blocked.
The standard says that the device have to be pushed next to a wall, so i hope that there is a cop-out for us this time - there will be space left for the airflow.